This site displays a prototype of a “Web 2.0” version of the daily Federal Register. It is not an official legal edition of the Federal Register, and does not replace the official print version or the official electronic version on GPO’s govinfo.gov.
The documents posted on this site are XML renditions of published Federal Register documents. Each document posted on the site includes a link to the corresponding official PDF file on govinfo.gov. This prototype edition of the daily Federal Register on FederalRegister.gov will remain an unofficial informational resource until the Administrative Committee of the Federal Register (ACFR) issues a regulation granting it official legal status. For complete information about, and access to, our official publications and services, go to About the Federal Register on NARA's archives.gov.
The OFR/GPO partnership is committed to presenting accurate and reliable regulatory information on FederalRegister.gov with the objective of establishing the XML-based Federal Register as an ACFR-sanctioned publication in the future. While every effort has been made to ensure that the material on FederalRegister.gov is accurately displayed, consistent with the official SGML-based PDF version on govinfo.gov, those relying on it for legal research should verify their results against an official edition of the Federal Register. Until the ACFR grants it official status, the XML rendition of the daily Federal Register on FederalRegister.gov does not provide legal notice to the public or judicial notice to the courts.
Pipeline and Hazardous Materials Safety Administration (PHMSA); DOT.
Notice; issuance of advisory bulletin.
This advisory bulletin advises owners and operators of petroleum gas and natural gas facilities of the need to take the appropriate steps to prevent damage to pipeline facilities from accumulated snow or ice. Past events on natural gas distribution system facilities appear to have been related to either the stress of snow and ice or the malfunction of pressure control equipment due to ice blockage of pressure control equipment vents. This advisory reminds owners and operators of the need to take precautionary actions to prevent adverse events.Start Further Info
FOR FURTHER INFORMATION CONTACT:
Linda Daugherty, Deputy Associate Administrator for Policy and Programs at 202-366-4595 or by e-mail at Linda.Daugherty@dot.gov.End Further Info End Preamble Start Supplemental Information
The accumulation of snow and ice increases the potential for damage to meters and regulators and other aboveground pipeline facilities and components. Incidents have occurred in past winters on natural gas distribution system facilities that appear to have been related to either the stress of snow and ice or malfunction of pressure control equipment due to ice blockage of pressure control equipment vents. Exposed piping at metering and pressure regulating stations, at service regulators, and at propane tanks, are at greatest risk. Damage may result from the stresses imposed by the additional loading of the snow or ice. Damage to facilities may also result from the impact of snow or ice falling from roofs, ice forming in or on regulators preventing their proper operation, or shoveling snow from roofs to protect dwellings from abnormal snow accumulation.
II. Advisory Bulletin (ADB-11-02)
To: Owners and Operators of Petroleum Gas and Natural Gas Facilities in Areas Subject to Heavy Snowfall or Abnormally Icy Weather.
Subject: Dangers of Abnormal Snow and Ice Build-up on Gas Distribution Systems.
Purpose: To remind owners and operators of the need to (1) monitor the potential impact of excessive snow and ice on these facilities; and (2) inform the public about possible hazards from snow and ice accumulation on regulators and other pipeline facilities.
Advisory: PHMSA is advising operators of petroleum gas and natural gas pipeline facilities, regardless of whether those facilities are regulated by PHMSA or state agencies, to consider the following steps to address the safety risks from accumulated snow and ice on pipeline facilities:
1. Notify customers and other entities of the need for caution associated with excessive accumulation and removal of snow and ice. Notice should include the need to clear snow and ice from exhaust and combustion air vents for gas appliances to:
(a) Prevent accumulation of carbon monoxide in buildings; or
(b) Prevent operational problems for the combustion equipment.
2. Pay attention to snow and ice related situations that may cause operational problems for pressure control and other equipment.
3. Monitor the accumulation of moisture in equipment and snow or ice blocking regulator or relief valve vents which could prevent regulators and relief valves from functioning properly.
4. The piping on service regulator sets is susceptible to damage that could result in failure if caution is not exercised in cleaning snow from around the equipment. Where possible, use a broom instead of a shovel to clear snow off regulators, meters, associated piping, propane tanks, tubing, gauges or other propane system appurtenances.
5. Remind the public to contact the gas company or designated emergency response officials if there is an odor of gas present or if gas appliances are not functioning properly. Also, remind the public that they should leave their residence immediately if they detect a gas or propane odor and report the odor Start Printed Page 7239to their gas company, propane operator or designated emergency response officials.Start Signature
Issued in Washington, DC, on February 3, 2011.
Deputy Associate Administrator for Policy and Programs.
[FR Doc. 2011-2837 Filed 2-8-11; 8:45 am]
BILLING CODE 4910-60-P